An increasingly common power saving practice in data center thermal management is to swap out air cooling unit blower fans with electronically commutated plug fans, Although, both are centrifugal blowers. The blade design changes: forward versus backward curved with peak static efficiencies of 60% and 75%, respectively, which results in operation power savings. The side effects of which are not fully understood. Therefore, it has become necessary to develop an overall understanding of backward curved blowers and compare the resulting flow, pressure, and temperature fields with forwarding curved ones in which the induced fields are characterized, compared, and visualized in a reference data center which may aid data center planning and operation when making the decisions of which computer room air handler (CRAH) technology to be used. In this study, experimental and numerical characterization of backward curved blowers is introduced. Then, a physics-based computational fluid dynamics model is built using the 6sigmaroom tool to predict/simulate the measured fields. Five different scenarios were applied at the room level for the experimental characterization of the cooling units and another two scenarios were applied for comparison and illustration of the interaction between different CRAH technologies. Four scenarios were used to characterize a CRAH with backward curved blowers, during which a CRAH with forwarding curved was powered off. An alternate arrangement was examined to quantify the effect of possible flow constraints on the backward curved blower's performance. Then parametric and sensitivity of the baseline modeling are investigated and considered. Different operating conditions are applied at the room level for experimental characterization, comparison, and illustration of the interaction between different CRAH technologies. The measured data is plotted and compared with the computational fluid dynamics (CFD) model assessment to visualize the fields of interest. The results show that the fields are highly dependent on CRAH technology. The tile to CRAH airflow ratios for the flow constraints of scenarios 1, 2, 3, and 4 are 85.5%, 83.9%, 61%, and 59%, respectively. The corresponding leakage ratios are 14.5%, 16%, 38.9%, and 41%, respectively. Furthermore, the validated CFD model was used to investigate and compare the airflow pattern and plenum pressure distribution. Lastly, it is notable that a potential side effect of backward curved technology is the creation of an airflow dead zone.